1Due to the limited availability of the products in stock, shipping will end when the stock is out.
2It might not be able to repair our products when replacement parts become unavailable, regardless of the maintenance period.
1The backlight burnout detection function is not supported.
2Please refer to the GP-Pro EX reference manual for details on font types and character codes.
3Other font sizes can be set up with the Editor software.
1When using in an environment where the temperature becomes or exceeds 40 °C for an extended period of time, the screen contrast level may decrease from its original level of brightness.
1Capacity available for user application.
2Application memory can provide 128KB for Data Backup. For further information, please refer to the GP-Pro EX reference manual.
3Set up the “Clock Updates“ feature with the Editor software. Please refer to the GP-Pro EX reference manual “Common” - “Clock Update Settings” for details.
1If connecting a bar code reader to the GP, be sure to supply power from an external source (such as a self-powered hub).
If you supply power from the GP, the GP may reset itself because the GP cannot supply enough power.
1The front face of the unit, installed in a solid panel, has been tested using conditions equivalent to the standards shown in the specification. Even though the unit's level of resistance is equivalent to these standards, oils that should have no effect on the unit can possibly harm the unit. This can occur in areas where either vaporized oils are present, or where low viscosity cutting oils are allowed to adhere to the unit for long periods of time. If the unit's front face protection sheet becomes peeled off, these conditions can lead to the ingress of oil into the unit and separate protection measures are suggested. Also, if non-approved oils are present, it may cause deformation or corrosion of the front panel's plastic cover. Therefore, prior to installing the unit, be sure to confirm the type of conditions that will be present in the unit's operating environment. If the installation gasket is used for a long period of time, or if the unit and its gasket are removed from the panel, the original level of the protection cannot be guaranteed. To maintain the original protection level, be sure to replace the installation gasket regularly.
2For dimensional tolerance, everything +1/-0 mm [+0.04/-0 in.] and R in angle are below R3 [R0.12 in.]. Even if the installation wall thickness is within the recommended range for the "Panel Cut Dimensions", depending on wall's material, size, and installation location of GP unit and other devices, the installation wall could warp. To prevent warping, the installation surface may need to be strengthened.