rh._.exports({"0":[[" ","設定例10"]],"2":[[" ","接続機器","の通信設定はエンジニアリングソフト(EcoStruxure \n Machine Expert – HVAC)で行います。"," ","接続機器","の設定"," ","エンジニアリングソフトを起動します。"," ","メニューバーから[ファイル] -> [新規プロジェクト]をクリックします。"," ","表示器","選択のプルダウンメニューでM172 \n\t 28-42 I/Os 596.11","※1","を選択し、任意のプロジェクト名で[OK]をクリックします。"," ","※1","型式の末尾に付加される数値は、F/Wバージョンを表します。エンジニアリングツールのバージョンによっては異なる場合があります。また、「M172 \n\t 28-42 I/Os」は以下のようにお使いのコントローラーに置き換えられます。"," ","コントローラー名"," ","表示器名"," ","M172O / M172P"," ","M172 07-18 I/Os"," ","M172 28-42 I/Os"," ","M171P Flush"," ","M171P Flush Mounting"," ","M171P"," ","M171P Blind"," ","M171P Display"," ","PCと対象コントローラーの間にUSBケーブル(A - mini-B)を接続します。"," ","メニューバーから[オンライン] -> [通信設定…]をクリックします。"," ","[Modbus]を有効にし、[プロパティ]をクリックして、Modbusの通信設定を行います。"," ","USBポートを選択します。"," ","[シミュレーション]タブに移動します。"," ","[ターゲットの接続]ボタンをクリックします。"," ","ツリーメニューから[M172 28-42 I/Os] -> \n\t [BIOSパラメーター] -> [全てのパラメーター]の順に展開し、[Ethernet]フォルダーを選択します。"," ","設定パラメーターは以下のとおりです。"," ","名前"," ","設定値"," ","備考"," ","Port_ETH_PI"," ","502"," ","Modbusポート番号"," ","Ip_1_ETH_PI"," ","192"," ","IPアドレス"," ","この場合は、「192.168.1.110」を表しています"," ","Ip_2_ETH_PI"," ","168"," ","Ip_3_ETH_PI"," ","1"," ","Ip_4_ETH_PI"," ","110"," ","DefGtwy_1_ETH_PI"," ","0"," ","デフォルトゲートウェイ"," ","この場合は、「0.0.0.0」を表しています"," ","DefGtwy_2_ETH_PI"," ","0"," ","DefGtwy_3_ETH_PI"," ","0"," ","DefGtwy_4_ETH_PI"," ","0"," ","NetMsk_1_ETH_PI"," ","255"," ","ネットワークマスク"," ","この場合は、「255.255.255.0」を表しています"," ","NetMsk_2_ETH_PI"," ","255"," ","NetMsk_3_ETH_PI"," ","255"," ","NetMsk_4_ETH_PI"," ","0"," ","メニューバーから[パラメーター] -> [全て書き込み]をクリックします。"," ","電源のオフ/オンでコントローラーをリセットします。"," ","MEMO"," ","HVACコントローラーを使用する場合は、ドライバーのプロパティの[機器設定]で[HVACコントローラーを使用]にチェックをつけてください。"," ","文字列変数を使用する場合は、ドライバのプロパティの[文字列モード]から[先頭アドレスから\"BADC\"]を選択してください。使用可能な文字コードはASCIIのみです。"," ","[HVACコントローラーを使用]にチェックをつけると、以下のプロパティが無効になります。","\n\t\t- アドレスモード","\n\t\t- IEC61131シンタックス","\n\t\t- モード","\n\t\t- 通信最適化","\n\t\t- 使用するフレーム長","\n\t\t- Length"," ","このドライバは、EcoStruxure Machine Expert - HVACからエクスポートされた変数を使用します。","BLUE","の変数エディターのツールバーから[インポート]をクリックして、エクスポートされた変数をインポートします。"," ","接続機器","のユニットIDを0～255の整数で入力します。"]],"3":[[" ","接続機器"]],"id":"14"})