rh._.exports({"0":[[" ","設定例2"]],"1":[[" ","設定例"]],"2":[[" ","接続機器","の通信設定にはControl \n Techniques設定ツール(CTSoft Ver.01.10.02)をお使いください。詳細は","接続機器","のマニュアルを参照してください。"," ","設定ツールを起動します。"," ","プロジェクトを新規作成します。"," ","ツリービューで、使用するスロット番号に対して、[バラメータ]から[SM-Applications \n\t Plus]を選択して、ダイアログボックスを表示します。"," ","設定するパラメータをダブルクリックして、[Edit Parameter]ダイアログボックスを表示します。"," ","以下の各項目を設定して、[OK]をクリックします。"," ","Parameter"," ","設定項目"," ","設定値"," ","05"," ","RS-485 address"," ","1"," ","06"," ","RS-485 mode"," ","15"," ","07"," ","RS-485 baud rate"," ","6: 19200"," ","08"," ","RS-485 turnaround delay"," ","2"," ","09"," ","RS-485 Tx enable delay"," ","OFF"," ","通信設定を","接続機器","にダウンロードします。"," ","接続機器","をリセットします。"," ","通信設定を","接続機器","に保存します。"," ","接続機器","を再起動します。"," ","MEMO"," ","接続機器のユニットIDを「1 ～ 247」で設定してください。"]],"id":"10"})