rh._.exports({"0":[[" ","設定例3"]],"1":[[" ","接続機器","の設定"]],"2":[[" ","接続機器","の設定には、ディップスイッチ設定とラダープログラムが必要です。"],[" ","モード設定スイッチ"," ","設定"," ","設定項目"," ","0"," ","オンライン"," ","交信条件設定スイッチ"," ","ディップスイッチ"," ","設定"," ","設定項目"," ","SW1"," ","OFF"," ","TCPタイムアウトエラー時の回線処理選択"," ","SW2"," ","OFF"," ","データコード設定"," ","SW3"," ","OFF"," ","Y19に従い動作する"," ","SW4"," ","OFF"," ","使用不可（OFF固定）"," ","SW5"," ","OFF"," ","使用不可（OFF固定）"," ","SW6"," ","OFF"," ","使用不可（OFF固定）"," ","SW7"," ","ON"," ","CPU交信タイミング設定"," ","SW8"," ","OFF"," ","イニシャルタイミング設定"],[" ","自動オープンUDPポート番号（デフォルト：5000）で通信する場合の例を示します。"," ","接続機器","のIPアドレス"," ","：192.168.0.1"," ","接続機器","のポート番号"," ","：5000"," ","MEMO"," ","この機能で通信する場合、PLCでIPアドレスとポート番号を指定する必要はありません。"," ","上記サンプルは","表示器","とUDP通信するための最小のラダーです。その他エラー処理やTCP通信等の詳細については、","接続機器","のマニュアルをご参照ください。"]],"3":[[" ","スイッチ設定"],[" ","ラダープログラム例"]],"id":"4"})