rh._.exports({"0":[[" ","設定例6"]],"1":[[" ","接続機器","の設定"]],"2":[[" ","接続機器","の設定は接続するポートによって異なります。"],[" ","ラダーソフトのツールバーの[オプション]から[PLCシステムレジスタ設定]を選択し、[PLCシステムレジスタ設定]ダイアログボックスを表示します。[ツールポート設定]タブを選択して下記のように設定を行います。通信設定に関する詳細は","接続機器","のマニュアルを参照してください。"," ","ラダーソフトの設定"," ","設定項目"," ","設定値"," ","通信速度"," ","19200"," ","データ長"," ","8"," ","モデム接続"," ","しない"," ","動作モード設定スイッチ"," ","SW1：OFF"," ","ユニットNo."," ","1"," ","動作モード設定スイッチ"," ","ディップ"," ","スイッチ"," ","設定"," ","設定内容"," ","SW1"," ","OFF"," ","伝送速度：19,200bps"],[" ","ラダーソフトのツールバーの[オプション]から[PLCシステムレジスタ設定]を選択し、[PLCシステムレジスタ設定]ダイアログボックスを表示します。[COMポート設定]タブを選択して下記のように設定を行います。通信設定に関する詳細は","接続機器","のマニュアルを参照してください。"," ","設定項目"," ","設定値"," ","通信速度"," ","19200"," ","データ長"," ","8"," ","パリティチェック"," ","奇数"," ","ストップビット"," ","1"," ","通信モード"," ","コンピュータリンク"," ","モデム接続する"," ","OFF"," ","ユニットNo."," ","1"],[" ","ユニット背面の伝送フォーマット設定スイッチを下記の様に設定します。"," ","ディップスイッチ"," ","設定"," ","設定内容"," ","SW1"," ","ON"," ","システム予約"," ","SW2"," ","ON"," ","COM1側伝送速度"," ","19200bps"," ","SW3"," ","OFF"," ","SW4"," ","ON"," ","COM1側データ長：8ビット"," ","SW5"," ","ON"," ","システム予約"," ","SW6"," ","ON"," ","COM2側伝送速度"," ","19200bps"," ","SW7"," ","OFF"," ","SW8"," ","ON"," ","COM2側データ長：8ビット"],[" ","ユニット背面の局番設定スイッチを [1] に設定し、伝送フォーマット設定スイッチを下記の様に設定し ます。"," ","ディップスイッチ"," ","設定"," ","設定内容"," ","SW1"," ","ON"," ","COM1側動作モード"," ","コンピュータリンク"," ","SW2"," ","ON"," ","SW3"," ","ON"," ","COM1側伝送速度"," ","19200bps"," ","SW4"," ","OFF"," ","SW5"," ","ON"," ","COM2側動作モード"," ","コンピュータリンク"," ","SW6"," ","ON"," ","SW7"," ","ON"," ","COM2側伝送速度"," ","19200bps"," ","SW8"," ","OFF"," ","MEMO"," ","AFP2465はFP2/FP2SHのマルチコミュニケーションユニットです。","\n\t\tAFP2803はAFP2465に装着する通信ブロックです。"]],"3":[[" ","CPU上のツールポートを使用する場合"],[" ","CPU上のRS232Cポートを使用する場合"],[" ","コンピュータコミュニケーションユニットAFP2462を使用する場合"],[" ","マルチコミュニケーションユニットAFP2465と通信ブロックAFP2803を組み合わせて使用する場合"]],"id":"69"})