rh._.exports({"0":[[" ","設定例11"]],"1":[[" ","接続機器"]],"2":[[" ","LSエレクトリックの設定ツール(XG-PD Editor)を使用して、","接続機器","の通信設定を指定します。"," ","詳細は","接続機器","のマニュアルを参照してください。"," ","設定ツールを起動します。"," ","[File]メニューから[New File]を選択し、XGBプロジェクトを作成します。"," ","MEMO"," ","接続機器","からプロジェクトを読出すには、[Open \n\t\t\t from PLC...]を選択します。"," ","[Online]メニューから[Connect]を選択します。"," ","[Online]メニューから[Read IO Information]を選択します。"," ","[Standard settings]タブで[Cnet]をダブルクリックして、[Standard Settings-Cnet]ダイアログボックスを表示します。"," ","[Channel 2]設定項目を以下のように設定し、[OK]をクリックします。"," ","設定項目"," ","設定値"," ","Type"," ","RS485"," ","Speed"," ","38400"," ","Data Bit"," ","8"," ","Stop Bit"," ","1"," ","Parity Bit"," ","NONE"," ","Modem Type"," ","Null Modem"," ","Station"," ","0"," ","Active Mode"," ","XGT server"," ","[Online]メニューから[Write Parameter]を選択して、[Write Parameter]ダイアログボックスを表示します。"," ","使用するモジュール選択し、[OK]をクリックします。"," ","[Online]メニューから[Reset]を選択します。"]],"id":"23"})