rh._.exports({"2":[[" ","表示器"," ","（接続ポート）"," ","ケーブル"," ","備考"," ","GP-4116 (COM1)"," ","3E"," ","自作ケーブル"," ","ケーブル長：500m以内"," ","SP5000 (COM1/2)","SP5000X (COM1/2)","ST6000","※c-2"," (COM2)","ST-6200 (COM1)","ST6000 2nd Gen","※d-4"," ","※d-5"," (COM2)","PFXST6200AWADI","※d-4"," (COM1)","STM6000 (COM1)","PS6000ベーシックボックス (COM1/2)"," ","3F"," ","シュナイダーエレクトリック製RS-422端子台変換アダプタ"," ","PFXZCBADTM1"," ","+"," ","自作ケーブル"," ","ケーブル長：500m以内"," ","3A"," ","シュナイダーエレクトリック製COMポート変換アダプタ(COM1用)"," ","CA3-ADPCOM-01"," ","+"," ","シュナイダーエレクトリック製コネクタ端子台変換アダプタ"," ","CA3-ADPTRM-01"," ","+"," ","自作ケーブル"," ","3B"," ","自作ケーブル"," ","PS5000","PS6000 (オプションインターフェイス)","PSA6000"," ","※6"," ","3G"," ","自作ケーブル"," ","ケーブル長：500m以内"," ","※c-2","ST-6200を除く"," ","※d-4","COM ポートの仕様上、フロー制御に制限があるため、結線図を読み替える必要があります。"," ","使用できる制御信号に制限がある表示器について"," ","※d-5","PFXST6200AWADIを除く"," ","※6","RS-422/485(4線式)で通信できるCOMポートのみ使用できます。"," ","IPC"," \n COM Port"," ","MEMO"," ","接続ケーブルには、中国電線工業株式会社のダブルシールド0-VCTF-SS 2C*0.75mm2、中国電線工業株式会社のダブルシールドUL2464-DSS 2C x 20AWG、および倉茂電工株式会社のUL2464-2SB 2 x 20AWGを推奨します。"," ","接続機器","本体のFG端子はD種接地を行ってください。"," ","FGのシールドケーブルへの接続は、設置環境に応じて","接続機器","または","表示器","のどちらかで行ってください。"," ","通信ケーブルを接続する際には、信号用グランド(SG)を必ず接続してください。"," ","RS422の接続では、株式会社ジェイテクトのマニュアルでケーブル長を確認してください。"," ","危険"," ","感電"," ","装置を接続する前に、相互接続する装置の各コンポーネントの接地接続が、同じグランドポテンシャル(100オーム以内)に確実に接続されていることを確認してください。"," ","上記の指示に従わないと、死亡や重傷を招くおそれがあります。"," ","警告"," ","意図しない機器操作"," ","シールデッドツイストペアケーブルを使用してください。"," ","ケーブルシールドを接続し、次にケーブルを","表示器","側のシングルポイントグラウンドに接続します。"," ","上記の指示に従わないと、死亡、重傷、または物的損害を負う可能性があります。"," ","\n      &amp;amp;lt;p&amp;amp;gt;&amp;amp;amp;#160;&amp;amp;lt;/p&amp;amp;gt;\n    "]],"3":[[" ","結線図 3"]],"id":"48"})