rh._.exports({"0":[[" ","Modbus SIOスレーブ"]],"1":[[" ","コマンドフォーマット"]],"2":[[" "],[" ","  表示"," "," ","接続構成","通信設定","結線図","使用可能デバイス","コマンドフォーマット"],[" ","重要",":"," ","1台の","表示器","(","SP-5B10","を除く)で複数のドライバを使用する場合、以下の制限があります。"," ","Rockwell Automation, \n\t\t Inc.のDH-485ドライバを同時に使用することはできません。"," ","Schneider Electric \n\t\t SAのUni-Telwayドライバを同時に使用することはできません。"," ","Siemens AGのSIMATIC \n\t\t S7 MPI直結ドライバを同時に使用することはできません。"," ","本ドライバ（通信速度38400以上）をCOM1とCOM2の両方で使用することはできません。"," ","1：1接続"," ","n：1接続の場合"," ","MEMO"," ","表示器","（スレーブ）の接続可能台数は","接続機器","によって異なります。","接続機器","の仕様を確認してください。"],[" ","シュナイダーエレクトリック","が推奨する","表示器","と","接続機器","の通信設定例を示します。"," ","警告"," ","意図しない機器操作"," ","データの転送を正しく行えるように、このセクションの指示をよく読んで理解してください。"," ","上記の指示に従わないと、死亡、重傷、または物的損害を負う可能性があります。"," ","\n&amp;lt;p&amp;gt;&amp;amp;#160;&amp;lt;/p&amp;gt;\n"],[" ","以下に示す結線図と","接続機器","のメーカーが推奨する結線図が異なる場合がありますが、"," ","本書に示す結線図でも動作上問題ありません。"," ","接続機器","本体のFG端子はD種接地を行ってください。詳細は","接続機器","のマニュアルを参照してください。"," ","表示器","内部でSGとFGは接続されています。","接続機器","とSGを接続する場合は短絡ループが形成されないようにシステムを設計してください。"," ","ノイズなどの影響で通信が安定しない場合はアイソレーションユニットを接続してください。"," ","\n&amp;lt;p&amp;gt;&amp;amp;#160;&amp;lt;/p&amp;gt;\n"],[" ","使用可能なデバイスアドレスの範囲を下表に示します。ただし、実際にサポートされるデバイスの範囲は","接続機器","によって異なりますので、ご使用の","接続機器","のマニュアルで確認してください。"," ","警告"," ","意図しない機器操作"," ","表示器","と","接続機器","プログラムから同じレジスタに同時に書込みを行わないでください。"," ","ビット単位でアクセスしているレジスタに16ビットのワード値を書込まないでください。"," ","上記の指示に従わないと、死亡、重傷、または物的損害を負う可能性があります。"," ","\n&amp;lt;p&amp;gt;&amp;amp;#160;&amp;lt;/p&amp;gt;\n"],[" ","本ドライバは以下のコマンドをサポートしています。"," ","機能"," ","ファンクションコード"," ","最大点数"," ","Read Coils"," ","0x01"," ","2000ビット"," ","Read Discrete Inputs"," ","0x02"," ","2000ビット"," ","Read Holding Registers"," ","0x03"," ","125ワード"," ","Read Input Registers"," ","0x04"," ","125ワード"," ","Write Single Coils"," ","0x05"," ","1 bit"," ","Write Single Register"," ","0x06"," ","1ワード"," ","Diagnostics"," ","0x08 / 0x00, 0x00"," ","-"," ","Write Multiple Coils"," ","0x0F"," ","1968ビット"," ","Write Multiple Registers"," ","0x10"," ","123ワード"," ","Mask Write Register"," ","0x16"," ","1ワード"," ","Read/Write Multiple Registers"," ","0x17"," ","読出し：125ワード"," ","書込み：121ワード"," ","Read Device Identification","*1"," ","0x2B / 0x0E"," ","-"," ","*1 Read Device Identification"," ","オブジェクトID"," ","オブジェクト名"," ","備考"," ","0x00"," ","VendorName"," ","ベンダー名"," ","Pro-face"," ","0x01"," ","ProductCode"," ","プロダクトコード。機器設定の[プロダクトコード]を設定していない場合は、機種名が返信されます。"," ","例 ","ST-6500WAD"," ","0x02"," ","MajorMinorRevision"," ","ランタイムバージョン"," ","例 3.0.0.42"," ","0x03"," ","VendorUrl"," ","ベンダーURL"," ","www.pro-face.com"," ","0x04"," ","ProductName"," ","プロダクト名"," ","BLUE"," ","0x05"," ","ModelName"," ","機種名"," ","例 ","ST-6500WAD"," ","0x06"," ","UserApplicationName"," ","プロジェクト名 / ターゲット名"," ","例 Project1/Target01"," ","Modbus SIO スレーブ"]],"6":[[" ","接続構成"],[" ","通信設定"],[" ","結線図"],[" ","使用可能デバイス"]],"id":"35"})