rh._.exports({"0":[[" ","設定例3"]],"1":[[" ","接続機器","の設定"]],"2":[[" ","接続機器","の通信設定はプログラミングソフト（MELSOFT GX Works3）で行います。"," ","詳細は","接続機器","のマニュアルを参照してください。"," ","プログラミングソフトを起動します。"," ","ナビゲーションウィンドウの[ユニット情報]から対象となるリンクI/Fの[ポート1ユニットパラメータ]設定ウィンドウを開きます。"," ","[基本設定]の[自ノード設定]で以下の設定を行います。"," ","設定項目"," ","設定内容"," ","IPアドレス"," ","192.168.3.40"," ","サブネットマスク"," ","255.255.255.0"," ","RUN中の書込み許可/禁止設定"," ","一括で許可する(SLMP)"," ","交信データコード"," ","バイナリ"," ","オープン方法の設定"," ","プログラムでOPENしない"," ","ネットワークNo./局番による交信"," ","無効"," ","[相手機器接続構成設定]の[詳細設定]をクリックすると、[Ethernet構成]ウィンドウが表示されます。"," ","[ユニット一覧]ウィンドウの[Ethernet機器(汎用)]エリアで[SLMP接続機器]を選択し、設定画面にドラッグ&ドロップします。"," ","設定画面の[SLMP接続機器]で以下の設定を行います"," ","設定項目"," ","設定内容"," ","プロトコル"," ","UDP"," ","シーケンサポート番号"," ","1025"," ","生存確認"," ","UDP"," ","設定内容を保存し[ユニットパラメータ]設定ウィンドウの[適用]をクリックします。"," ","プロジェクトを保存し、","接続機器","に送信します。","\n\t[ユニットパラメータ]がチェックされていることを確認してください。"," ","接続機器","の電源をOFF/ONするかまたは変更が有効であることを確認するために","接続機器","をリセットします。"," ","MEMO"," ","IPアドレスに関してはネットワーク管理者に確認してください。同一ネットワークで重複するIPアドレスを設定しないでください。"]],"id":"2"})