rh._.exports({"0":[[" ","設定例2"]],"1":[[" ","接続機器","の設定"]],"2":[[" ","通信設定は、基本設定用専用ツール（Resource Configurator）およびラダーソフト（Logic Designer）で行います。"," ","<通信モジュールの通信設定>"," ","接続機器","のIPアドレスを「192.168.1.1」に設定します。"," ","MEMO"," ","接続機器","のIPアドレスの設定方法はFCN/FCJの基本設定用専用ツール（Resource \n\t\t\t Configurator）のオンラインヘルプを参照してください。"," ","基本設定用専用ツールを起動します。"," ","［ファイル］メニューから［接続］を選択し、［接続］ダイアログボックスを表示します。"," ","［ホスト名］に「192.168.1.1」を入力します。"," ","［ユーザ名］と［パスワード］を入力してログインします。"," ","［コントローラ構成］のツリービューから使用するリンクI/Fを選択します。"," ","［ポート名］にポート名を入力します。"," ","［コントローラ構成］のツリービューの使用するリンクI/Fから［Port1］を選択します。"," ","伝送仕様を以下のように設定します。"," ","伝送仕様"," ","設定値"," ","結線方式"," ","-"," ","通信方式"," ","Full-duplex"," ","伝送速度"," ","19200"," ","データビット"," ","8"," ","パリティ設定"," ","EVEN"," ","ストップビット"," ","1"," ","送信入力信号監視"," ","NONE"," ","受信フロー制御"," ","NONE"," ","通信エラーAPI通知"," ","YES"," ","通信設定を","接続機器","にダウンロードします。"," ","接続機器","を再起動します。"," ","<制御ロジックのダウンロード手順>"," ","ラダーソフトを起動します。"," ","MODBUS通信（RTUモード）スレーブ機能の起動を行うために、制御ロジックを作成します。制御ロジック例については、「制御ロジック例」を参照してください。"," ","制御ロジック例"," ","[PORT］横の['COM1']をダブルクリックし、[変数のプロパティ]ダイアログボックスを表示します。"," ","［名前］に接続するポート名を入力し、［OK］をクリックします。"," ","[STATION］横の[UNIT#1]をダブルクリックし、[変数のプロパティ]ダイアログボックスを表示します。"," ","［名前］に接続するステーション番号を入力し、［OK］をクリックします。"," ","［ビルド］メニューから［プロジェクトの再コンパイル］を選択します。"," ","プロジェクトツリーウィンドウの[Target Setting]をダブルクリックし、［ターゲット設定］ダイアログボックスを表示します。"," ","[ホスト名/IPアドレス]に「192.168.1.1」を入力します。"," ","[OK]をクリックします。"," ","通信設定を","接続機器","にダウンロードします。"," ","接続機器","を再起動します。"],[" ","表示器","と","接続機器","を接続するには制御ロジックが必要です。"," ","以下に制御ロジック例を示します。"," ","MEMO"," ","接続機器のユニットIDを「1 ～ 247」で設定してください。"]],"4":[[" ","制御ロジック例"]],"id":"19"})