rh._.exports({"0":[[" ","Modbus TCPスレーブ"]],"1":[[" ","コマンドフォーマット"]],"2":[[" "],[" ","  表示"," "," ","接続構成","通信設定","使用可能デバイス","コマンドフォーマット"],[" ","1:1接続の場合"," ","1:n接続の場合"," ","MEMO"," ","接続機器","(マスター)の最大接続台数は20台です。"," ","n:1接続の場合"," ","MEMO"," ","表示器","(スレーブ)の接続可能台数は","接続機器","によって異なります。","接続機器","の仕様を確認してください。"," ","n:m接続の場合"," ","MEMO"," ","表示器","(スレーブ)間の通信はありません。"," ","表示器","(スレーブ)の接続可能台数は","接続機器","によって異なります。","接続機器","の仕様を確認してください。"," ","接続機器","(マスター)の最大接続台数は20台です。"," ","イーサネットスイッチ/イーサネットHUB"," ","番号"," ","名前"," ","備考"," ","(1)"," ","Scneider Electric製490 NTWケーブル"," ","ModbusスレーブTCP/IPを使用すると、","接続機器","に最大20のマスターコントローラを接続できます。"," ","(2)"," ","Schneider Electric製イーサネットスイッチ/イーサネットHUB"," ","499 NEH 181 00"," ","499 NEH 104 10"," ","499 NEH 251 00"," ","(3)"," ","10BASE-T自動イーサネット"," ","イーサネットモジュールまたは内蔵イーサネットポート"," ","番号"," ","名前"," ","備考"," ","(1)"," ","Scneider Electric製490 NTC 000ケーブル"," ","ModbusスレーブTCP/IPを使用すると、","接続機器","に最大20のマスターコントローラを接続できます。"],[" ","シュナイダーエレクトリック","が推奨する","表示器","と","接続機器","の通信設定例を示します。"," ","警告"," ","意図しない機器操作"," ","データの転送を正しく行えるように、このセクションの指示をよく読んで理解してください。"," ","上記の指示に従わないと、死亡、重傷、または物的損害を負う可能性があります。"," ","\n&amp;lt;p&amp;gt;&amp;amp;#160;&amp;lt;/p&amp;gt;\n"],[" ","使用可能なデバイスアドレスの範囲を下表に示します。ただし、実際にサポートされるデバイスの範囲は","接続機器","によって異なりますので、ご使用の","接続機器","のマニュアルで確認してください。"," ","警告"," ","意図しない機器操作"," ","表示器","と","接続機器","プログラムから同じレジスタに同時に書込みを行わないでください。"," ","ビット単位でアクセスしているレジスタに16ビットのワード値を書込まないでください。"," ","上記の指示に従わないと、死亡、重傷、または物的損害を負う可能性があります。"," ","\n&amp;lt;p&amp;gt;&amp;amp;#160;&amp;lt;/p&amp;gt;\n"],[" ","本ドライバは以下のコマンドをサポートしています。"," ","機能"," ","ファンクションコード"," ","最大点数"," ","Read Coils"," ","0x01"," ","2000ビット"," ","Read Discrete Inputs"," ","0x02"," ","2000ビット"," ","Read Holding Registers"," ","0x03"," ","125ワード"," ","Read Input Registers"," ","0x04"," ","125ワード"," ","Write Single Coils"," ","0x05"," ","1ビット"," ","Write Single Register"," ","0x06"," ","1ワード"," ","Write Multiple Coils"," ","0x0F"," ","1968ビット"," ","Write Multiple Registers"," ","0x10"," ","123ワード"," ","Mask Write Register"," ","0x16"," ","1ワード"," ","Read/Write Multiple Registers"," ","0x17"," ","読出し：125ワード"," ","書込み：121ワード"," ","Read Device Identification","*1"," ","0x2B / 0x0E"," ","-"," ","*1 Read Device Identification"," ","オブジェクトID"," ","オブジェクト名"," ","備考"," ","0x00"," ","VendorName"," ","ベンダー名"," ","Pro-face"," ","0x01"," ","ProductCode"," ","プロダクトコード。機器設定の[プロダクトコード]を設定していない場合は、機種名が返信されます。"," ","例 ","ST-6500WAD"," ","0x02"," ","MajorMinorRevision"," ","ランタイムバージョン"," ","例 3.0.0.42"," ","0x03"," ","VendorUrl"," ","ベンダーURL"," ","www.pro-face.com"," ","0x04"," ","ProductName"," ","プロダクト名"," ","BLUE"," ","0x05"," ","ModelName"," ","機種名"," ","例 ","ST-6500WAD"," ","0x06"," ","UserApplicationName"," ","プロジェクト名 / ターゲット名"," ","例 Project1/Target01"," ","Modbus TCP スレーブ"]],"5":[[" ","接続構成"],[" ","通信設定"],[" ","使用可能デバイス"]],"id":"2"})