rh._.exports({"0":[[" ","設定例7"]],"1":[[" ","接続機器","の設定"]],"2":[[" ","接続機器","の通信設定は調節計前面のステーション番号設定スイッチとパラメータローダソフトウェア（PUM Loader）で行います。"," ","詳細は","接続機器","のマニュアルを参照してください。"," ","ステーション番号設定スイッチを「0」に設定します。"," ","MEMO"," ","ステーション番号設定スイッチで設定した値に1を足した値がステーション番号になります。"," ","パラメータローダソフトウェアを起動します。"," ","[モジュール分類選択]ダイアログボックスで[制御/イベント/アナログモジュール]を選択します。"," ","[OK]をクリックします。"," ","[モード選択]ダイアログボックスで任意のモードを選択します。"," ","[OK]をクリックします。"," ","メインウィンドウのツリービューで[制御モジュール]-[パラメータ]-[通信]を選択します。"," ","設定する項目をダブルクリックし、設定値の選択ダイアログボックスを表示します。"," ","設定値を選択します。"," ","[OK]をクリックします。"," ","通信設定を","接続機器","に転送します。"],[" ","設定項目"," ","設定値"," ","RS-485パリティ設定"," ","なし"," ","RS-485通信速度設定"," ","19.2Kbps"," ","RS-485通信許可設定"," ","1"," ","RS-485応答インターバル時間設定"," ","1"," ","拡張通信モジュール(PUMC)接続許可"," ","0"]],"4":[[" ","設定値"]],"id":"26"})