rh._.exports({"0":[[" ","設定例13"]],"1":[[" ","接続機器"]],"2":[[" ","エンジニアリングソフトEcoStruxure Machine Expert – HVACを使用して、","接続機器","の通信設定を行います。"," ","エンジニアリングソフトを起動します。"," ","メニューバーから[ファイル] -> [新規プロジェクト]をクリックします。"," ","表示器選択のプルダウンメニューでM172 28-42 I/Os \n\t 596.11","※1","を選択し、任意のプロジェクト名で[OK]をクリックします。"," ","※1","型式の末尾に付加される数値は、F/Wバージョンを表します。エンジニアリングツールのバージョンによっては異なる場合があります。また、「M172 \n\t 28-42 I/Os」は以下のようにお使いのコントローラーに置き換えられます。"," ","コントローラー名"," ","表示器名"," ","M172O / M172P"," ","M172 07-18 I/Os"," ","M172 28-42 I/Os"," ","M171P Flush"," ","M171P Flush Mounting"," ","M171P"," ","M171P Blind"," ","M171P Display"," ","PCと対象コントローラーの間にUSBケーブル(A - mini-B)を接続します。"," ","メニューバーから[オンライン] -> [通信設定…]をクリックします。"," ","[Modbus]を有効にし、[プロパティ]をクリックして、Modbusの通信設定を行います。"," ","USBポートを選択します。"," ","[シミュレーション]タブに移動します。"," ","[ターゲットの接続]ボタンをクリックします。"," ","ツリーメニューから[M172 28-42 I/Os] -> \n\t [BIOSパラメーター] -> [全てのパラメーター]の順に展開し、[RS485-1 On Board]フォルダーを選択します。"," ","設定"," ","フォルダー"," ","M172上のRS485-2ポート"," ","RS485-2 On Board"," ","M171上のRS485ポート"," ","RS485 On Board"," ","シリアルリンクモジュール上のRS485ポート"," ","RS485 Plugin Passive"," ","設定パラメーターは以下のとおりです。"," ","名前","※1"," ","設定値"," ","備考"," ","Addr_RS485_OB1"," ","1"," ","Modbusポート番号"," ","Proto_RS485_OB1"," ","3"," ","3=Modbus/RTU"," ","DataBit_RS485_OB1"," ","8"," ","データビット"," ","StopBit_RS485_OB1"," ","1"," ","ストップビット"," ","Parity_RS485_OB1"," ","2"," ","パリティビット"," ","0=なし、1=奇数、2=偶数"," ","Baud_RS485_OB1"," ","2"," ","ボーレート"," ","0=9600"," ","1=19200"," ","2=38400"," ","3=57600"," ","4=76800"," ","5=115200"," ","※1","パラメーター名は選択したフォルダによって異なります。"," ","RS485-1 On Board"," ","RS485-2 On Board"," ","RS485 On Board"," ","RS485 Plugin Passive"," ","Addr_RS485_OB1"," ","Addr_RS485_OB"," ","Addr_RS485_OB"," ","Addr_RS485_OB"," ","Proto_RS485_OB1"," ","Proto_RS485_OB"," ","Proto_RS485_OB"," ","Proto_RS485_OB"," ","DataBit_RS485_OB1"," ","DataBit_RS485_OB"," ","DataBit_RS485_OB"," ","DataBit_RS485_OB"," ","StopBit_RS485_OB1"," ","StopBit_RS485_OB"," ","StopBit_RS485_OB"," ","StopBit_RS485_OB"," ","Parity_RS485_OB1"," ","Parity_RS485_OB"," ","Parity_RS485_OB"," ","Parity_RS485_OB"," ","Baud_RS485_OB1"," ","Baud_RS485_OB"," ","Baud_RS485_OB"," ","Baud_RS485_OB"," ","メニューバーから[パラメーター] -> [全て書き込み]をクリックします。"," ","電源のオフ/オンでコントローラーをリセットします。"," ","MEMO"," ","HVACコントローラーを使用する場合は、ドライバーのプロパティの[機器設定]で[HVACコントローラーを使用]にチェックをつけてください。"," ","文字列変数を使用する場合は、ドライバのプロパティの[文字列モード]から[先頭アドレスから\"BADC\"]を選択してください。使用可能な文字コードはASCIIのみです。"," ","[HVACコントローラーを使用]にチェックをつけると、以下のプロパティが無効になります。","\n\t\t- アドレスモード","\n\t\t- IEC61131シンタックス","\n\t\t- モード","\n\t\t- 通信最適化","\n\t\t- 使用するフレーム長","\n\t\t- Length"," ","このドライバは、EcoStruxure Machine Expert - HVACからエクスポートされた変数を使用します。","BLUE","の変数エディターのツールバーから[インポート]をクリックして、エクスポートされた変数をインポートします。"," ","接続機器のユニットID を「1 ～ 247」で設定してください。"]],"id":"118"})