rh._.exports({"0":[[" ","結線図 10"]],"1":[[" ","表示器"," ","（接続ポート）"," ","ケーブル"," ","備考"," ","SP5000 (COM1/2)","\nSP5000X (COM1/2)","\nST6000","※b-3"," (COM2)","\nST-6200 (COM1)","\nST6000 2nd Gen","※d-4"," ","※d-5"," (COM2)","\nPFXST6200AWADI","※d-4"," (COM1)","\nSTM6000 (COM1)","\nPS6000ベーシックボックス (COM1/2)"," ","10A"," ","自作ケーブル"," ","ケーブル長：1000m以内."," ","GP-4116 (COM1)"," ","10B"," ","自作ケーブル"," ","ケーブル長：1000m以内."," ","PS5000","PS6000 (オプションインターフェイス)","PSA6000"," ","※8"," ","10C"," ","自作ケーブル"," ","ケーブル長：1000m以内."," ","※b-3","ST-6200を除く"," ","※d-4","COM ポートの仕様上、フロー制御に制限があるため、結線図を読み替える必要があります。"," ","使用できる制御信号に制限がある表示器について"," ","※d-5","PFXST6200AWADIを除く"," ","※8","RS-422/485(2線式)で通信できるCOMポートのみ使用できます。"," ","IPC"," COMポートについて"," ","重要",":"," ","RS-422/485ケーブル長は、","接続機器","によりますが、通常1000m以内になります。詳細は","接続機器","のマニュアルを参照してください。"," ","接続方法と終端抵抗は","接続機器","によって異なります。"," ","表示器","の終端抵抗はアイソレーションされていません。"," ","危険"," ","感電"," ","装置を接続する前に、相互接続する装置の各コンポーネントの接地接続が、同じグランドポテンシャル(100オーム以内)に確実に接続されていることを確認してください。"," ","上記の指示に従わないと、死亡や重傷を招くおそれがあります。"," ","警告"," ","意図しない機器操作"," ","シールデッドツイストペアケーブルを使用してください。"," ","ケーブルシールドを接続し、次にケーブルを","表示器","側のシングルポイントグラウンドに接続します。"," ","上記の指示に従わないと、死亡、重傷、または物的損害を負う可能性があります。"," ","\n      &amp;amp;lt;p&amp;amp;gt; &amp;amp;lt;/p&amp;amp;gt;\n    "]],"id":"67"})