rh._.exports({"0":[[" ","SIMATIC S7 MPIダイレクト"]],"1":[[" ","使用できる接続機器のデータタイプ"]],"2":[[" "],[" ","  表示"," "," ","接続構成","通信設定","結線図","使用可能デバイス","使用できる接続機器のデータタイプ"],[" ","重要",":"," ","1台の","表示器","(","SP-5B10","を除く)で複数のドライバを使用する場合、以下の制限があります。"," ","Modbus OrganizationのModbus SIOスレーブドライバ（通信速度38400以上）を同時に使用することはできません。"," ","Rockwell Automation, Inc.のDH-485ドライバを同時に使用することはできません。"," ","Schneider Electric SAのUni-Telwayドライバを同時に使用することはできません。"," ","本ドライバをCOM1とCOM2の両方で使用することはできません。"," ","MEMO"," ","1つの接続構成にS7-300/400シリーズとS7-200シリーズ、S7-1200シリーズを混在させることができます。"," ","1つの接続構成にPROFIBUS DP対応機器とMPI対応機器を混在させることは推奨しません。"," ","1:1接続"," ","n:m接続"," ","MEMO"," ","n:m接続の場合、","表示器","と","接続機器","の台数は以下の条件を満たす範囲となります。"," ","接続機器","1台に接続できる","表示器","は最大64台です。"," ","接続機器","1台に接続できる","表示器","の最大台数は","接続機器","の種類によって異なります。通信設定に関する詳細は","接続機器","のマニュアルを参照してください。"],[" ","シュナイダーエレクトリック","が推奨する","表示器","と","接続機器","の通信設定例を示します。"," ","警告"," ","意図しない機器操作"," ","データの転送を正しく行えるように、このセクションの指示をよく読んで理解してください。"," ","上記の指示に従わないと、死亡、重傷、または物的損害を負う可能性があります。"," ","\n&amp;lt;p&amp;gt; &amp;lt;/p&amp;gt;\n"],[" ","以下に示す結線図と","接続機器","のメーカーが推奨する結線図が異なる場合がありますが、"," ","本書に示す結線図でも動作上問題ありません。"," ","接続機器","本体のFG端子はD種接地を行ってください。詳細は","接続機器","のマニュアルを参照してください。"," ","表示器","内部でSGとFGは接続されています。","接続機器","とSGを接続する場合は短絡ループが形成されないようにシステムを設計してください。"," ","ノイズなどの影響で通信が安定しない場合はアイソレーションユニットを接続してください。"," ","\n&amp;lt;p&amp;gt; &amp;lt;/p&amp;gt;\n"],[" ","使用可能なデバイスアドレスの範囲を下表に示します。ただし、実際にサポートされるデバイスの範囲は","接続機器","によって異なりますので、ご使用の","接続機器","のマニュアルで確認してください。"," ","警告"," ","意図しない機器操作"," ","表示器","と","接続機器","プログラムから同じレジスタに同時に書込みを行わないでください。"," ","ビット単位でアクセスしているレジスタに16ビットのワード値を書込まないでください。"," ","上記の指示に従わないと、死亡、重傷、または物的損害を負う可能性があります。"," ","\n&amp;lt;p&amp;gt; &amp;lt;/p&amp;gt;\n"],[" ","BLUE","で使用できる","接続機器","のデータタイプは次のとおりです。"," ","S7-200"," ","S7-300/400"," ","S7-1200"," ","BOOL"," ","SINT/USINT/BYTE"," ","INT/UINT/WORD"," ","DINT/UDINT/DWORD"," ","REAL"," ","LREAL"," ","-"," ","-"," ","TIME"," ","-"," ","-"," ","DATE"," ","-"," ","-"," ","TIME_OF_DAY"," ","-"," ","-"," ","DATE_AND_TIME"," ","-"," ","-"," ","STRING"," ","MEMO"," ","接続機器","のシリーズを変更すると、新しいシリーズでサポートされていないデータタイプに関連している変数はエラーになります。"," ","SIMATIC S7 MPI 直結"]],"3":[[" ","接続構成"],[" ","通信設定"],[" ","結線図"],[" ","使用可能デバイス"]],"id":"10"})