rh._.exports({"0":[[" ","設定例5"]],"1":[[" ","接続機器","の設定"]],"2":[[" ","LSエレクトリックの設定ツール(XG-PD Editor)を使用して、","接続機器","の通信設定を指定します。"," ","詳細は","接続機器","のマニュアルを参照してください。"," ","?"," ","設定ツールを起動します。"," ","モジュールを使用してオフラインで[Standard settings]タブから接続されているベースとスロットを選択します。[Communication Module Settings]ダイアログボックスが表示されます。"," ","[Type]から\"Cnet\"を選択し、[OK]をクリックします。"," ","[Online]メニューから[Connect]を選択します。"," ","[Online]メニューから[Read IO Information]を選択します。"," ","[Standard settings]タブで[Cnet]をダブルクリックします。[Standard Settings-Cnet]ダイアログボックスが表示されます。"," ","[Channel 1]設定項目を以下のように設定し、[OK]をクリックします。"," ","設定項目"," ","設定値"," ","Type"," ","RS485"," ","Speed"," ","38400"," ","Data Bit"," ","8"," ","Stop Bit"," ","1"," ","Parity Bit"," ","NONE"," ","Modem Type"," ","Null Modem"," ","Station"," ","0"," ","Active Mode"," ","XGT server"," ","[Online]メニューから[Write Parameter]を選択します。[Write Parameter]ダイアログボックスが表示されます。"," ","モジュールを使用して選択し、[OK]をクリックします。"," ","[Online]メニューから[Reset]を選択します。"]],"id":"19"})