rh._.exports({"0":[[" ","調節計MODBUS SIO"]],"2":[[" "],[" ","  表示"," "," ","接続構成","通信設定","結線図","使用可能デバイス"],[" ","1:1接続"," ","1:n接続"," ","MEMO"," ","接続機器","の最大接続台数は31台です。"],[" ","シュナイダーエレクトリック","が推奨する","表示器","と","接続機器","の通信設定例を示します。"," ","警告"," ","意図しない機器操作"," ","データの転送を正しく行えるように、このセクションの指示をよく読んで理解してください。"," ","上記の指示に従わないと、死亡、重傷、または物的損害を負う可能性があります。"," ","\n&amp;lt;p&amp;gt;&amp;amp;#160;&amp;lt;/p&amp;gt;\n"],[" ","以下に示す結線図と","接続機器","のメーカーが推奨する結線図が異なる場合がありますが、"," ","本書に示す結線図でも動作上問題ありません。"," ","接続機器","本体のFG端子はD種接地を行ってください。詳細は","接続機器","のマニュアルを参照してください。"," ","表示器","内部でSGとFGは接続されています。","接続機器","とSGを接続する場合は短絡ループが形成されないようにシステムを設計してください。"," ","ノイズなどの影響で通信が安定しない場合はアイソレーションユニットを接続してください。"," ","\n&amp;lt;p&amp;gt;&amp;amp;#160;&amp;lt;/p&amp;gt;\n"],[" ","使用可能なデバイスアドレスの範囲を下表に示します。ただし、実際にサポートされるデバイスの範囲は","接続機器","によって異なりますので、ご使用の","接続機器","のマニュアルで確認してください。"," ","警告"," ","意図しない機器操作"," ","表示器","と","接続機器","プログラムから同じレジスタに同時に書込みを行わないでください。"," ","ビット単位でアクセスしているレジスタに16ビットのワード値を書込まないでください。"," ","上記の指示に従わないと、死亡、重傷、または物的損害を負う可能性があります。"," ","各パラメータのメモリマップは以下のように記載されています。"," ","<ビットデータの例>"," ","ビットデータ（読出専用）：ファンクションコード [02H]"," ","相対アドレス"," ","コイル番号※1"," ","タイプ"," ","メモリ内容"," ","読出しデータ"," ","0000H"," ","10001"," ","ビット"," ","警報1ON/OFF"," ","0:警報1OFF \n\t\t1:警報1ON"," ","0001H"," ","10002"," ","（予約）"," ","0002H"," ","10003"," ","（予約）"," ","0003H"," ","10004"," ","（予約）"," ","0004H"," ","10005"," ","ビット"," ","警報2ON/OFF"," ","0:警報2OFF、 \n\t\t1:警報2ON"," ","0005H"," ","10006"," ","（予約）"," ",":"," ",":"," ",":"," ",":"," ",":"," ","※1 コイル番号が","表示器","で指定するアドレスとなります。"," ","例：ビットデータのコイル番号 10001 のパラメータ「警報1ON/OFF」の場合、表示器で指定するアドレスは、以下の通りとなります。コイル番号(00001 \n ～、10001 ～)は、上1 桁をデバイスとして指定します。"," ","例：ワードデータのレジスタ番号 41003 のパラメータ「前面制御SV 値」の場合、表示器で指定するアドレスは、以下の通りとなります。レジスタ番号(30001 \n ～、40001 ～、31001 ～、41001 ～)は、上2 桁をデバイスとして指定する。"," ","MEMO"," ","接続機器","のパラメータデータは伝送データ上では小数点なしのデータになります。従って、表示器ではそのデータの小数点位置合わせの処理が必要です。例えば小数点付きで数値表示する場合は、[表示設定]タブの[小数点桁数]を設定する必要があります。また、","接続機器","への書込みの場合は、設定する値（小数点付）を整数にした値を書込む必要があります。"," ","\n\t\t例） レジスタ番号41025 の「出力1 下限リミット」の場合。"," ","接続機器","値/設定値： \n\t\t 3.00%"," ","表示器","値/設定値： \n\t\t 300"," ","\n\t\t各パラメータの設定値範囲（小数点付きか否か）の詳細については、","接続機器","のマニュアルを参照してください。"," ","\n&amp;lt;p&amp;gt;&amp;amp;#160;&amp;lt;/p&amp;gt;\n"," ","調節計 MODBUS SIO"]],"5":[[" ","接続構成"],[" ","通信設定"],[" ","結線図"],[" ","使用可能デバイス"]],"id":"37"})