rh._.exports({"0":[[" ","設定例6"]],"1":[[" ","接続機器","の設定"]],"2":[[" ","接続機器","の通信設定は","接続機器","のディップスイッチとロータリースイッチ、ラダーソフト（CX-Programmer）で行います。IPアドレスの設定は自動生成方式(動的)で行います。"," ","詳細は","接続機器","のマニュアルを参照してください。"],[" ","ディップスイッチ"," ","設定値"," ","内容"," ","SW1"," ","OFF"," ","ユーザメモリに書込みできるかどうかを設定します。"," ","ON ：書き込み不可"," ","OFF : 書き込み可"," ","SW2"," ","OFF"," ","電源ON時にメモリカードからデータを読込むかどうかを設定します。"," ","ON ：読み込む"," ","OFF ：読み込まない"," ","SW3"," ","OFF"," ","未使用"," ","SW4"," ","OFF"," ","未使用"," ","SW5"," ","OFF"," ","シリアルポートの通信速度を設定します。"," ","ON ：ラダーソフト（ツールバス）の通信速度を自動認識します。"," ","OFF ：ラダーソフトの通信設定にしたがいます。"," ","SW6"," ","OFF"," ","特殊補助リレーA395.12 の状態を切り替えます。"," ","SW7"," ","OFF"," ","簡易バックアップの種類を設定します。"," ","SW8"," ","OFF"," ","OFFに固定"],[" ","設定項目"," ","設定内容"," ","ユニットNo."," ","0"," ","設定項目"," ","設定内容"," ","NODE No."," ","x 16","1"," ","0"," ","x 16","0"," ","1"],[" ","ラダーソフトを起動します。"," ","[ファイル]メニューから[新規作成]を選択し、[PLC機種変更]ダイアログボックスを表示します。"," ","[PLC機種]から使用する","接続機器","を選択します。"," ","[PLC機種]から[設定]をクリックし、[PLC機種の設定]ダイアログボックスを表示します。"," ","[CPU形式]から使用するCPU形式を選択し、[OK]をクリックします。"," ","[ネットワーク種別]から接続方法を選択します。"," ","[OK]をクリックします。"," ","ワークスペースのツリービューから[I/Oテーブル・ユニット設定]をダブルクリックし、[PLCのI/Oテーブル]ダイアログボックスを表示します。"," ","ツリービューの[内蔵ポート/インナーボード]から設定する内蔵EtherNet/IPポートをダブルクリックし、[パラメータの編集]ダイアログボックスを表示します。"," ","[TCP/IP]タブで[IPアドレス]と[サブネットマスク]を以下のように設定します。"," ","設定項目"," ","設定内容"," ","IPアドレス"," ","192.168.0.1"," ","サブネットマスク"," ","255.255.255.0"," ","[FINS/TCP]タブで[FINS/TCPポート]を以下のように設定します。"," ","設定項目"," ","設定内容"," ","FINS/TCPポート"," ","初期値(9600)"," ","[OK]をクリックします。"," ","通信設定を","接続機器","に転送します。"," ","接続機器","を再起動します。"],[" ","IPアドレスとサブネットマスクに関してはネットワーク管理者に確認してください。重複するIPアドレスは設定しないでください。"," ","重複するノード番号は設定しないでください。"]],"3":[[" ","ディップスイッチの設定"],[" ","ロータリスイッチの設定"],[" ","ラダーソフトの設定"],[" ","備考"]],"id":"16"})