rh._.exports({"0":[[" ","設定例3"]],"1":[[" ","接続機器","の設定"]],"2":[[" ","MELSEC-Aシリーズ(イーサネットインターフェースユニット)が表示器と通信するには、","接続機器","のラダープログラムとイーサネットインターフェースユニットのディップスイッチを設定する必要があります。サンプルラダープログラムとディップスイッチの設定は以下のとおりです。"," ","詳細は","接続機器","のマニュアルを参照してください。"],[" ","LD"," ","M9038"," ","DMOVP"," ","Hxxxxxxxx  D100"," ",": ","接続機器","のIPアドレス","※1"," ","MOVP"," ","K0  D102"," ","MOV"," ","H0100  D116"," ",": 接続方法(UDP)"," ","MOV"," ","K1024  D124"," ",": ","接続機器","のポート番号(「1024」と入力する場合など)"," ","MOV"," ","K1024  D127"," ",": 表示器のポート番号(「1024」と入力する場合など)"," ","DMOV"," ","Hxxxxxxxx  D125"," ",": 表示器のIPアドレス","※1"," ","DMOV"," ","HFFFFFFFF  D128"," ","MOV"," ","HFFFF  D130"," ","LD"," ","M9036"," ","TOP"," ","H0000  H0000  D100  K50"," ","LD"," ","X19"," ","MOV"," ","K5  D113"," ","TOP"," ","H0000  K13  D113  K1"," ","LD"," ","M9036"," ","OUT"," ","Y0019"," ",": イニシャル要求信号"," ","LD"," ","M9036"," ","OUT"," ","Y0008"," ",": オープン要求信号"," ","END"," ","※1",":"," ","xxxxxxxxはIPアドレスを示します(HEX表示)。IPアドレスに関してはネットワーク管理者に確認してください。同一ネットワークで重複するIPアドレスを設定しないでください。"," ","重要",":"," ","接続機器","の通信設定に使用しているアドレス(上記の例ではD100以上)を設定で表示器のシステムエリアの先頭アドレスに繰り返し使用しないでください。"],[" ","モード設定スイッチ"," ","設定値"," ","設定内容"," ","0"," ","オンライン"," ","交信条件設定スイッチ"," ","ディップスイッチ"," ","設定値"," ","設定内容"," ","SW1"," ","OFF"," ","TCPタイムアウトエラー時の回線処理選択"," ","SW2"," ","OFF"," ","データコード設定"," ","SW3"," ","ON"," ","CPU交信タイミング設定"," ","SW4"," ","OFF"," ","イニシャルタイミング設定"," ","MEMO"," ","IPアドレスに関してはネットワーク管理者に確認してください。同一ネットワークで重複するIPアドレスを設定しないでください。"," ","接続機器","のデータコードスイッチは必ずOFF(バイナリコード)にしてください。"," ","接続機器","の運転中に表示器から書き込みを行うときは、書き込み可に設定します。"]],"3":[[" ","ラダープログラム例"],[" ","インタフェースユニットの設定"]],"id":"4"})