rh._.exports({"0":[[" ","機器"]],"1":[[" ","- マニュアルナビゲーション -"," ","マニュアルトップページ"," ","クイックツアー"," ","対応機種/機能一覧"," ","機能ガイド"," ","制限事項"," ","機器接続マニュアル"," ","ハードウェアマニュアル"," ","エラーメッセージ一覧"," ","更新されたマニュアルとダウンロードリンク"," ","Home"," ",">"," ","プロパティ"," ",">"," ","ソースプロパティ"," ",">"," ","機器"],[" ","プロパティ"," ","説明"," ","データの種類"," ","最小値"," ","最大値"," ","読み出し"," ","書き込み"," ","保持"," ","ErrorFlag","通信エラーが発生すると、このフラグに真がセットされます。"," ","エラーを確認した後に手動でフラグをリセットしてください。"," ","ブール"," ","-"," ","-"," ","-"," ","ErrorStatus","通信エラー状態がセットされます。"," ","0: エラーなし"," ","1: エラーあり"," ","2: 未使用 (通信スキャンオフ時)"," ","通信エラーが復旧した場合、デッドバンドに設定した時間が経過してから [","ErrorStatus","] に 0 がセットされます。"," ","デッドバンドはドライバーの [機器] プロパティウィンドウの [エラーステータスデッドバンド (秒)] で設定してください。"," ","整数"," ","-"," ","-"," ","-"," ","-"," ","IPAddress.CurrentValue","*2","機器の現在の IP アドレス"," ","DWORD"," ","1"," ","4294967295"," ","-"," ","IPAddress.OverWriteValue","*2","機器に設定する IP アドレス。スクリプトで [機器] オペレーションを使用して保存が実行されたとき、この値は関連する機器の IP アドレスに適用されます。"," ","機器"," ","DWORD"," ","1"," ","4294967295"," ","-"," ","ScanOffStatus","*1","現在の機器の通信スキャン状態。"," ","True: 通信スキャンが停止しています。"," ","False: 機器の通信スキャンが実行されています。"," ","MEMO:"," 機器の通信スキャンをオフにすると、その機器に関連する変数のクオリティが「bad」となり、その変数を使用しているオブジェクトに通信エラーを示す赤枠が表示されます。"," ","ブロックスクリプトでクオリティが「bad」の変数が使用されていると、そのブロックスクリプトは実行されません。クオリティが「bad」の変数を使用するブロックスクリプトの動作については、以下を参照してください。"," ","ブロックの種類"," ","ブール"," ","-"," ","-"," ","-"," ","-"," ","ScanOffControl","*1","保存や再起動せずに機器の通信スキャンを ON / OFF します。"," ","False: 通信スキャンをオンにします。"," ","True: 通信スキャンをオフにします。"," ","ブール"," ","-"," ","-"," ","UnitId.CurrentValue","*2","現在のユニット ID を表示します。"," ","(Modbus SIO マスタードライバー / Modbus SIO ASCII マスタードライバー)"," ","UINT"," ","1"," ","247"," ","-"," ","現在のユニット ID を表示します。"," ","(Modbus TCP マスタードライバー)"," ","UNIT"," ","0"," ","255"," ","-"," ","UnitId.OverWriteValue","*2","機器に必要なユニット ID を設定します。スクリプトで [機器] オペレーションを使用して保存が実行されたとき、この値は関連する機器のユニット ID に適用されます。"," ","(Modbus SIO マスタードライバー / Modbus SIO ASCII マスタードライバー)"," ","機器"," ","UNIT"," ","1"," ","247"," ","-"," ","機器に必要なユニット ID を設定します。スクリプトで [機器] オペレーションを使用して保存が実行されたとき、この値は関連する機器のユニット ID に適用されます。"," ","(Modbus TCP マスタードライバー)"," ","機器"," ","UNIT"," ","0"," ","255"," ","-"," ","*1 以下のドライバーの機器ではソースプロパティはサポートされていません。"," ","Modbus Organization"," ","Modbus SIO スレーブ"," ","Modbus TCP スレーブ"," ","Pro-face by Schneider Electric"," ","メモリーリンクイーサネット"," ","メモリーリンク SIO"," ","Schneider Electric"," ","EcoStruxure Augmented Operator Advisor"," ","*2 以下のドライバーの機器でソースプロパティがサポートされています。"," ","Modbus Organization"," ","Modbus SIO ASCII マスター"," ","Modbus SIO マスター"," ","Modbus TCP マスター"," ","Schneider Electric"," ","Modbus SIO マスター"," ","Modbus TCP マスター"," ","Copyright (C) 2025 シュナイダーエレクトリックホールディングス株式会社. 著作権保有"," |","BLUE 4.2 (マニュアルバージョン: 4.2.0.000)","| ","ユーザーガイド"]],"2":[[" ","機器"]],"id":"327"})